FREE Shipping with orders over $199 (details)
Doulton Ceramic Filter Elements have been trusted by relief organizations around the globe for over 150 years. These filters were developed in 1850 to remove disease causing baceria from London's Thames River.
These cleanable filter elements are designed to remove suspended solids and pathogenic bacteria. The ceramic shell composition and manufacture have been delicately balanced to control flow rate, the maximum pore size and element hardness.
The ceramic contains a specially formulated self-sterilizing silver compound and, therefore, the Sterasyl element does not require sterilization after cleaning. The silver content is precisely controlled to keep well within the maximum levels recommended by the World Health Organization and the E.P.A. The cartridge conforms to NSF Standard (number 53) health benefits with respect to cyst, turbidity, particulate reduction, and self-sterilizing effects.
The candle has one threaded end and one rounded end. It fits only in housings with female threads inside the top cap.
|Maximum working pressure||125 psi (8.6 bars)|
|Maximum working temperature||100 °F (37.8 °C)|
|Minimum working temperature||40 °F (4.4 °C)|
|Recommended cleaning frequency||every 6 months or when flow rate is noticeably lower|
|Recommended change frequency||every 12 months|
|Contaminant Removal||The great majority of pathogenic (disease causing) bacteria and cysts are larger than one µ. The pore size of the ceramic filter element is controlled so that it will remove all suspended matter larger than 0.9 µ.|
|Pathogenic Bacteria||Chorela, Typhoid, Salmonella, Serratia, E. Coli, Fecal Coliform: >99.99% removal|
|Cysts||Cryptosporidium parvum and Giardia lamblia: 100% removal (based on tests by Arizona State University)|
|Sediment||Down to 0.9 µ, 100%; 0.5-0.8 µ with a filter efficiency of >99.99% (based on tests by Spectrum Laboratories, Minneapolis, MN)|
|Dimensions:||10" (H) × 2" (D)
25.4 cm × 5.1 cm
|Maximum Working Pressure:||125 psig
|Working Temperature:||40 - 100 °F
4 - 38 °C
|Recommended Flow Rate:||0.5
|Recommended Cleaning Frequency:||Every 3 months or when water flow rate is noticeably lower||Recommended Change Frequency:||12 months or 1,000 gallons, whichever is sooner