FREE Shipping with orders over $99 (details)
Upgrade Your Faucet:
View All Styles and Colors
Tubing connection has never been easier than with Quick-Connect fittings. View our simplified Quick-Connect diagrams to see how...
Reverse osmosis drinking water systems include membrane separation, activated carbon absorption and conventional filtration to reduce the entire spectrum of contaminants that can be found in water. RO systems substantially remove heavy metals, such as barium, cadmium, chromium, lead and mercury; radium 226 / 228 selenium, cysts, chlorine, salts, turbidity and more!
Use our Bottled Water Cost Calculator to find out how much of an impact you have on the environment.
The innovative PURA twist and lock design makes service simple. Twist off the old cartridge and twist on the new. No messy sump removal. PURA DWS makes drinking water better and life easier.
Hydrotech's latest RO features quick-change cartridges, which can be customized for changing water conditions. These proprietary cartridges also simplify the regular replacement as required - typically on an annual basis. The QCRO delivers bottle water quality without the hassle or cost.
|Contaminant||Influent challenge concentration mg/L||Maximum permissible product water concentration mg/L||Minimum % Reduction||Average % Reduction|
|Arsenic||0.30 ± 10%||0.010||98.7||99.6|
|Barium||10.0 ± 10%||2.0||97.7||98.8|
|Cadmium||0.03 ± 10%||0.005||97.3||98.8|
|Chromium (+6)||0.3 ± 10%||0.1||97.6||99.1|
|Chromium (+3)||0.3 ± 10%||0.1||99.6||99.7|
|Copper||3.0 ± 10%||1.3||98.3||99.0|
|Fluoride||8.0 ± 10%||1.5||96.3||97.7|
|Lead||0.15 ± 10%||0.010||99.3||99.3|
|25 pCi/L ± 10%||5 pCi/L||80.0||80.0|
|Selenium||0.10 ± 10%||0.05||97.8||98.1|
|Turbidity||11 ± 1 NTU||0.5 NTU||96.7||98.9|
|TDS||750 ± 20%||187||84.5||85.1|
This system has been tested according to WQA S-300 for reduction of the substances listed above. The concentration of the indicated substances in water entering the system was reduced to a concentration less than or equal to the permissible limit for water leaving the system, as specified in NSF/ANSI 58 standard.